# How is cooling tower capacity measured

How to calculate the cooling capacity of a chiller. Chillers provide chilled water which is then used to provide air conditioning within buildings. The amount of cooling they produce varies and it’s important to know how much cooling a chiller is producing or is able to produce. **There is a video tutorial at the bottom of the page also.**

Firstly to perform this calculation we need to know a few things.

- The volume flow rate of water into the evaporator
- The inlet and outlet chilled water temperature

We then need to lookup the properties of water for the following

- The density of the water at the average temperature (inlet temp + outlet temp)/2
- The Specific Heat Capacity of the chilled water at the average temperature (inlet temp + outlet temp)/2

A recommended website to look these properties up is: PeaceSoftware.de

Let look at how to calculate the cooling capacity. We’ll first look at how to calculate in metric units and then imperial.

**Metric units:**

The water flow rate of chilled water into the evaporator is 0.0995m3/s, the inlet temperature is 12*c and the outlet temperature is 6*c. This means the average temperature is 9*c so we lookup the water properties at this temperature to find the density of 999.78kg/m3 and a specific heat capacity of 4.19kJ/kg/K.

Using the energy equation of Q = ṁ x Cp x ΔT we can calculate the cooling capacity.

Q = (999.78kg/m3 x 0.0995m3/s) x 4.19kJ/kg/K x ((12*c+273.15K) – (6*c+273.15K))

*We add 273.15K to the celcius to convert it to units of Kelvin. The Specific heat capacity (Cp) is measured in units of kJ per kg per Kelvin.*

This gives us a final answer of Q = 2,500kW of cooling. Full calculations are shown below.

Now lets look at how to calculate the cooling capacity of a chiller in imperial units

**Imperial units:**

The flow rate of chilled water into the evaporator is measured as 12,649ft3/h and the chilled water inlet temperature is 53.6*F the outlet temperature is 42.8*F. The average temperature is 48.2*F so we need to calculate the water properties at this temperature.

A good website for this is peacesoftware.de the although we will need to convert the units to imperial so for that we will use Specific heat capacity and density of water

This will give us a specifi heat capacity of 1.0007643BTU/lb.F and density of 62.414lb/Ft3

Using the energy equation of Q = ṁ x Cp x ΔT we can calculate the cooling capacity.

Q = (16,649FT3/h x 62.414lb/ft3) x 1.0007643BTU/lb.F x (53.6F – 42.8F)

Giving us a cooling capacity of 8,533,364BTU/h. see full calculations below.

- Do people still like radio broadcasts
- What makes a good PowerPoint presentation
- What is meant by pure bending
- How do I pronounce the name Leprechaun
- What is VPC in Azure
- Why is light a stimulus
- Can a company perform AML without KYC
- Is Eric Ho legit or a scam
- What can I gift to my gf
- Do you say FAQ or FAQs
- Why do narcissists always doubt you
- Why and how are dimples formed
- How does social media corrupt human interaction
- Why do people need settlements for mesothelioma
- What are some good anti Feminist songs
- What is the folding furniture market
- Why did Disney fire Jeffrey Katzenberg
- Why is Aquaman so cool
- Does CTS provide accommodation during training